Free shipping. Skip to main content. Email to friends Share on Facebook - opens in a new window or tab Share on Twitter - opens in a new window or tab Share on Pinterest - opens in a new window or tab. Add to Watchlist. People who viewed this item also viewed. Picture Information.
|Published (Last):||10 February 2015|
|PDF File Size:||6.69 Mb|
|ePub File Size:||7.93 Mb|
|Price:||Free* [*Free Regsitration Required]|
Uniwersal Sp z o. Automatic control unit for one-gear fan is to carry out the time control programme and to control the fan operation according the following conditions temperature, humidity and air flow speed in the ventilation duct.
The unit also connects the fan motor to the electric circuit, protects from the effects of short circuits, overloads, one phase operation. Built-in fuse has additional capacity of safeguarding the equipment against short circuits up to 50kA. The unit is able to make evident breaks in electric circuits.
The differentiated operating voltage values take into the account the power supply voltage for signal converter. THE switchgear transparent door allows for controlling the motor switch activation and the position of operation mode connector.
Safeguarded by one-field fuse element. The switch-off safeguards the transformer and control. In position 0 of the switch, the fan motor operation control is switched off. To switch on the selected work type, the operator must set the SQ1 switch confirming the work type in the same position that work type switch SQ. One gear roof fans Automatic control unit for three-phase roof fan motor control voltage 24 V AC. F1 three-field fuse safeguard QM1 motor switch-off kM1 motor installation contactor H signalling light F2 motor circuit breaker, activated for protection of the control transformer and control circuits T control circuits transformer SQ work type switch cam switch SQ1 switch confirming the work type change X spring clamp strip X1 insulated ramified terminal in the power circuit X2 insulated ramified terminal in the control circuit.
One gear roof fans Automatic control unit for one-phase roof fan motor control voltage V AC. Automatic Control Unit for a group of one-gear roof fans is manufactured to order. The customer must specified types of fans making the group and the type of the input signal converter. On the specification basis, the manufacturer will select proper equipment for the self-acting control unit and specify the required protection settings with an electric diagram.
Q0 motor circuit breaker included in the control transformer protection and to control circuits protection. X1 insulated ramified terminals Drawing 5 One-gear roof fans Automatic control unit for a group of 4 roof fans with three-phase motors control voltage V AC.
One-gear roof fans Automatic control unit for a group of 4 roof fans with three-phase motors control voltage 24 V AC. Fuse element qL is adjusted for the motor power Safeguarded by three-field fuse element.
Fuse element qL is adjusted for the motor power M motor switch-off. Selection and value should match chart 1. M motor switch-off. Control circuit Safeguarded by one-field fuse element. The below diagrams present an example of controlling a group of 4 fans. Safeguarded by three-field fuse element. Fuse element qL is adjusted for the motor power.
Safeguarded by M switch-off with the range 0,,4A. Setting 0,25A. Current of electromagnetic trip activation [A]. Equipment list F1 three-field fusible cut-out F01 one-field fusible cut-out of the control circuit QM Equipment list F1 three-field fusible cut-out Q0 motor circuit breaker included in the control transformer protection and to control circuits protection T control circuits transformer QM
Артикулы Fael Luce
Skip to main content. Picture Information Free postage. Mouse over to zoom - Click to enlarge. Have one to sell?